APC UPS Check
The APC UPS Check provides basic and advanced APC UPS battery information.
Basic Check information
|Instances on a Device||1|
|Supported Systems/Applications||Any PowerNet-MIB Compliant Device from APC.|
|Device Class||Server - Generic, Other, Printer, Scanner/Camera, Switch/Router, and Server - Windows.|
|Failed||Please check that the correct SNMP community string is configured in Network Discovery for the device|
|201 Exception OID_TYPE_NOSUCHOBJECT||Missing OID object on the device for specific metric|
The status of the UPS battery.
A Battery Low (3) value indicates the UPS will be unable to sustain the current load, and its Checks will be lost if power is not restored.
|Time On||126.96.36.199.4.1.3188.8.131.52.2.1.2||The elapsed time since the UPS has switched to battery power.|
|Last Replaced||184.108.40.206.4.1.3220.127.116.11.2.1.3||The date when the UPS system's batteries were last replaced, in mm/dd/yy format. For Smart-UPS models, this value is originally set in the factory. When replacing the UPS batteries, the administrator should reset this value.|
|18.104.22.168.4.1.322.214.171.124.2.2.1||The remaining battery capacity expressed as a percentage.|
|Temperature||126.96.36.199.4.1.3188.8.131.52.2.2.2||The current internal UPS temperature, expressed in degrees Celsius.|
|Time Remaining||184.108.40.206.4.1.3220.127.116.11.2.2.3||The run time remaining before battery exhaustion.|
|Replace Indicator||18.104.22.168.4.1.322.214.171.124.2.2.4||Indicates if the UPS batteries need to be replaced.